A Variable Frequency Drive (VFD) controls the speed of an AC induction motor by controlling the power (voltage
and frequency) that supplies the motor. By reducing the motor speed to match
the needs of the application, VFDs have the potential to significantly save
energy and reduce operating costs for a variety of motor driven applications. Motor systems that should be evaluated for energy savings through the use of VFDs include:
- variable load motor systems where output is throttled or damped below full rated speed
- centrifugal fan, pump, or blower systems
- systems that meet either criteria above that operate frequently (e.g., > 2000 hrs/yr)
The potential energy savings derived from reducing
a motors power to manage its speed are approximated by the Affinity Laws.
These engineering laws are used to express the relationship between flow, head,
and consumed power in relation to shaft speed for pump and fan applications and
can be summarized as follows:
- change in flow is proportional to the change in shaft speed
- change in head (pressure) is proportional to the square of the change in shaft speed
- change in power consumed is proportional to the cube of the change in shaft speed
Energy Savings Example
To illustrate the relationship between motor speed
and consumed power, assume a 50hp centrifugal pump (95% efficiency) operating 4,067 hours per
year with a 75% load factor, and electric costs at $.07 / kWh, is using a throttling valve to regulate flow to 70% on average. Applying the third affinity law, the
yearly electric cost of the motor running at full rated (100%) shaft speed (or
flow) would be:
Annual Energy Cost (Throttling Valve) =
(hp/Emotor) * LF * 0.746
kW/hp * (% full rated shaft speed)3
* (annual operating hours) * (cost of electricity)
50hp/0.93 * 0.75 * 0.746 kW/hp * (1.0)3 * 4,067 hrs/yr. * $.07/kWh = $8,564 per year
The same system is represented below, except an ASD (97% efficiency) replaces the throttling valve to achieve the same flow regulation by varying the motor's rotational speed.
Annual Energy Cost (ASD) =
(hp/Emotor) * LF * 0.746 kW/hp * (% full rated shaft speed)3
* (annual operating hours) * (cost of electricity) * (1/EASD)
50hp/.93 * 0.75% * 0.746kW/hp * (0.7)3 * 4,067 hrs/yr. * $.07/kWh * 1/0.97 = $3,028 per year
Using the information from each scenario, potential savings are calculated: replacing the throttling valve with the ASD can achieve approximately 5,500 in annual energy cost savings. Nearly 65% energy cost savings is gained as a result of a 30% reduction in shaft speed (or flow). In other words,
small reductions in speed and flow can lead to significant energy cost savings.
For additional summary information, please see CEE Motor Efficiency, Selection, and Management: A Guidebook for Efficiency Programs.
VFD Energy Savings Resources
The following resources highlight the energy savings benefits of motor control through VFDs.
General Resources and Market Data
Application Guide for AC Adjustable Speed Drive Systems, National Electrical Manufacturers Association (NEMA), 2001.
Publication developed to assist users in proper selection and application of drives.
Motors, Pumps and Fans and Motors, Pumps, and Fans Publications, U.S. Department of Energy EERE ITP, 2010.
Links to tip sheets, sourcebooks, case studies, technical publications, and
software, fact sheets, market assessments, and repair docs.
States Industrial Motor Driven System Market Assessment: Charting a Roadmap to
Energy Savings for Industry, U.S. Department of Energy EERE ITP, 2009.
Summarizes US industrial motor system energy use by application, industry
sector, large plant, etc. The report additionally showcases savings achieved
through DOEs Motor Challenge program.
States Industrial Electric Motor Systems Market Opportunities Assessment,
U.S. Department of Energy, 1998, revised 2002. A market overview of US industrial motor systems inventory, opportunities for energy savings, and motor system
purchase and management practices.
Motor and Drive System Performance: A Sourcebook for Industry, U.S. Department of Energy, 2008. A technical overview of motor and drive systems,
performance opportunities, costs and economics.
Energy Efficiency Reference Guide, Natural Resources Canada, 2009. Technical application considerations including load characteristics and comparison
with conventional control methods.
Drivepower, E Source,
Technology Atlas Series, 1999. Comprehensive market and technical overview of
motor and drive market structure and penetration, end-use data and program
strategies, technology and efficiency, sizing, selection, maintenance and
repair. Requires subscription.
Primary Industrial Control
and Adjustable Speed Drive Index, NEMA, 2010. Relative reported sales
activity of 90% of the U.S. domestic market from 2001-2010.
Variable Frequency Drives,
NEEA, 2000. Comprehensive U.S. market study of VFD market penetration, sales,
and opportunities by industry and application type.
Energy Savings Brochures, Fact Sheets and Video
Each of the following brochures provides a short
introduction to VFD technology, including a definition and suitable
applications for VFDs, as well as calculated energy savings examples and case
Control Your energy costs with VFDs, Wisconsin Focus on Energy, 2009.
Efficiency Fact Sheet Adjustable Speed Motor Drives, Washington State University, Energy Program.
Pumps Optimization: Energy Efficiency within Industrial Facilities, BC Hydro Power Smart, 2011.
of Variable Frequency Drives for Fan and Pump Control, Natural Resources Canada, 2002.
Tips Pumping Systems, Pumping Systems Tip Sheet #11, U.S. Department
of Energy ITP program, 2007.
Air Guide to Savings, Efficiency Vermont.
Energy Savings Calculators
VFD Tech Tool, New Jersey's Clean Energy Program. Spreadsheet that calculates overall facility-wide energy
savings estimate for a range of facility types and multiple motors.
Calculator, Bonneville Power Administration. Spreadsheet tool for estimating the energy savings and simple
payback for ASD installations on fans and pumps.
the Performance of a Waste-to-Energy Facility, U.S. Department of Energy
EERE ITP, 1998. Inlet damper controls replaced with VFDs reduces facility
energy consumption by 34%, 3.6 GWh or $329,500 in annual savings. Simple
payback was less than 10 months.
Fan System Optimization Improves Performance and Saves Energy at a Chemical
Plant, U.S. Department of Energy EERE ITP, 2005. ASD modulation of
combustion fan yields energy savings of 76,400 MMBtu and $420,000 in annual
savings. Simple payback was less than 2 months.
ARC Resources Ltd., One Electric-Powered Plant Done and Another on the Way with Support from BC Hydro,
October 2011 Case study illustrating how variable frequency drives, high efficiency motors, and larger diameter pipes have saved 3.6 gigawatt hours annually.
Demix Construction Case Study, Natural Resources Canada, Heads Up Newsletter,
October 2010 Case study illustrating 450 GWh, $12K annual savings, 2-3 year
Dynamic Windows & Doors Make Efficient Use of Compressed Air Systems with VSDs and BC Hydro ,
January 2012 Case study illustrating an upgrade to variable speed units yielding savings of over $17,000 annually with a 1 year payback.
Freyby Foods Find Double-Digit Savings with VFDs and BC Hydro,
October 2011 Case study illustrating energy savings of over 1,000,000 kilowatts from sustainability planning and VFDs.
IPEX Inc. and BC Hydro use VFDs to Save Energy at Plastics Plant, August 2010 Case study illustrating an upgrade from operating three 75hp chillers to running one 25hp variable frequency drive motor coupled to a fan, savings of one million kWh per year.
Lafarge Canada Invests Half of R&D Budget in Sustainability Initiatives and Save 15.6 GWh with BC Hydro, October 2011 Case study illustrating the energy savings from incorporating large air receivers and a variable speed compressor.
MacKenzie Sawmill Takes Initiative with BC Hydro and Compressed Air Systems, June 2010 Case study illustrating how a Power Smart Compressed Air study, which cost $57,000 and was fully paid for by BC Hydro, identified 1.5 million kWh per year in potential savings.
Manufacturing Energy Savings with a Variable Frequency Drive and Support from MidAmerican Case study illustrating how power factor can increase through installing a VFD on an extruder, which showed that 40 percent of the extruders electricity
consumption was wasted through the clutch controller.
Minneapolis- St. Paul International Airport Uses New Constant Speed Motor Controller with Support from Xcel Energy, 2010 Case study illustrating the new Constant Speed Motor Controller rebate from Xcel Energy, savings 9,364 kWh annually while extended life expectancy of motor components.
New Motors Drive Big Cost Savings for Property Management Firm with Support from Xcel Energy, 2011 Case study illustrating property upgrades from higher-efficiency motors, variable frequency drives on the air-handling units, to domestic water booster pumps, earning rebates from Xcel Energy of $20,715 in 2010 alone.
North Memorial and Xcel Energy: A Healthy Approach to Motor and Drive Efficiency, 2011 Case study illustrating how a vortex damper failure resulted in replacement by variable speed drives and reduced their energy use by 30%.
Stella-Jones Inc. Finds Speedy Savings with VSDs in Compressed Air Systems, March 2010 Case study illustrating how a compressed air retrofit, including a new compressor, new variable speed drive, higher capacity receivers and repaired leaks, now uses less than one-third the electricity of the previous system.
Turning Water into Savings with Xcel Energy, 2011 Case study illustrating the City of Richfield Water Treatment Plant's 375,570 kWh of energy savings from upgrades to motors and VFDs.
Frequency Drives Energy Efficiency Reference Guide, Natural Resources Canada, 2009. Three industrial case studies covering VFD replacement of eddy current
drives, HVAC damper controls, and vacuum pump controls including annual cost
and kWh savings.
Variable Speed Drives Make
Cents, Hydraulic Institute (HI). Registration and download are free.
Ken Rackowski, Bluestone Energy Services, presented at NSTAR Technology Show,
June, 2009. Introduction to drive technology, applications, benefits, controls.
Online Periodicals That Cover VFDs
Drivesmag - industry forum that provides specially developed content written by industry experts regarding electronic speed control of electric motors.
Electrical Construction & Maintenance
- technical publication for electrical professionals in electrical contracting firms, industrial plants and commercial & institutional facilities.
Maintenance Technology - a resource for manufacturing, process and service operations for technical, business and professional-development needs of C&I engineers, managers and technicians.
Reliable Plant Published by Noria Corp., provides plant maintenance and reliability leaders resources including technical tips, lean and best practices, safety, and energy
Plant Engineering / Control
Engineering Published by CFE Media LLC (Content for Engineers),
provides the engineering community with research and information.